In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
ACI World Headquarters
38800 Country Club Dr.
Farmington Hills, MI
ACI Middle East Regional Office
Second Floor, Office # 02.01/07
The Offices 02 Building, One Central
Dubai World Trade Center Complex
Phone: +971.4.516.3208 & 3209
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Experience in the Use of the Accelerated Testing Procedure for the Control of Concrete During the Construction of Tunnel “Emisor Central” in Mexico City
Author(s): Roberto Sanchez-Trejo and
Publication: Special Publication
Appears on pages(s): 15-28
Keywords: ders; fresh accelerated tests; compressive strength; concretes; cylin-concrete;
quality control; sampling; tunnels.
Abstract:Over one million cubic meters of concrete were poured during the construction of a huge project known as Deep Drainage System designed to eliminate the risk of floods in Mexico City. The main structure of this system is a tunnel 49.8 km (30.95 miles) in length, 6.50 m (21' 4") in internal diameter, and with a 0.70 m (27 l/2") average thickness of concrete lining. The most outstanding part of the product control of concrete was carried out by testing specimens cured in boiling water (procedure B, ASTM C-684). More than 1700 samples, consisting each of four specimens, were tested. Two specimens of each sample were tested at 28 l/2 hours and two at 28 days. Functional relationships were establi the 28 day compressive strength from the 28 l/2 hour test, with very satis These relationships allowed to adjust proportions to the optimum amounts of in order to fulfill the strength requ specifications. shed for predicting the data obtained in factory results. opportunely the mix ingredient materials irements of the job
Click here to become an online Journal subscriber