In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Nondestructive Testing of Cable Ducts in
Concrete Columns and Walls Using the
Author(s): J. Staerke Clausen and A. Knudsen
Publication: Special Publication
Appears on pages(s): 253-262
Keywords: concrete columns; impact-echo; injection of ducts; nondestructive testing (NDT); voids.
Abstract:The appearance of cracks and spalling in concrete columns in a new
eight-story office building brought about concerns that the injection of the ducts in the columns was poor quality. The cracks were mainly present at one floor, and trial drillings into the ducts on columns with severe cracks disclosed the presence of water and loose gravel and aggregates. Opening a duct revealed that the duct was either partially empty, filled with compacted gravel, or fully grouted.
It was decided to use the impact-echo (IE) method to investigate the columns
Each column contains four ducts with a 25 mm (1 in.) diameter reinforcing bar for distribution of the shear stress at the lower and upper 1.0 m (3 ft) to each floor. Testing was performed for each 0.1 m (4 in.) elevation in these areas. The criterion to approve the injection was that at least 0.7 m (2 ft) of the column at the floor or the ceiling was fully injected. After testing the columns on 3 floors, it was decided to investigate the ducts in the walls of the three stairwells of the building, as they were vital for transferring the stresses of the reinforcement down through the building. Verification of the IE-system by drilling cores showed that is possible to distinguish between empty ducts, fully injected ducts, and ducts with compacted gravel. More than 35,000 measurements were made. The examination of the ducts showed that approximately 63% of tests at the top and approximately 86% at the bottom of the columns and walls indicated full injection.
Click here to become an online Journal subscriber