In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: FRP Retrofit of the Ring-Beam of a Nuclear Reactor Containment Structure
Author(s): M. Demers, A. Popovic, K. W. Neale,
S. Rizkalla, and G. Tadros
Publication: Special Publication
Appears on pages(s): 303-316
Keywords: concrete repair; fiber optic sensors; nuclear power plant; structural monitoring; surface-bonded FRPs
Abstract:The Gentilly-1 nuclear power plant, in Quebec, Canada, was decommissioned in 1978. Since that time, the containment structure has been used for the storage of the moderately contaminated nuclear reactor. The enforcement of more rigorous environmental regulations, as well as economic considerations, have raised the decommissioning period from 40 to 100 years, thus severely increasing the durability requirements for the structure. The containment structure, constructed of thick prestressed concrete, was in good condition except for the secondary concrete. The latter is a keystone for the durability of the structure because it fills the recesses and protects the terminations of the tendons against corrosion. The differential shrinkage caused cracking and debonding and, with freeze-thaw cycling over the years, the secondary concrete had to be removed and replaced. The ringbeam, at the top of the containment structure, was severely affected because the numerous tendons of the roof terminate at that level. The retrofit of the ring-beam consisted of replacing the secondary concrete with highquality shrinkage-compensated mortar and concrete, followed by FRP wrapping. The layout of the FRP wrap was designed to mitigate the adverse effects of the new secondary concrete shrinking-induced cracks. Most of the concrete cold joints were covered by the FRP wrap, which was anchored on the dome roof to provide an effective support.
Click here to become an online Journal subscriber