In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Chat with Us Online Now
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Prestressed Concrete Pipe Repair
Author(s): John R. Thurston and Thomas C. Fisher
Publication: Special Publication
Appears on pages(s): 151-160
Keywords: backfilling; concrete pipes; corrosion; finite element method; pipelines; prestressing steels; repairs; shotcrete; Construction
Abstract:This paper describes repairs on two prestressed concrete pipelines (inverted siphons) that were found to have distressed areas. The distressed areas included disbonded mortar coating, and corroded and broken prestressing wires. The siphons were dewatered, during January and part of February 1991, for repairs and inside inspection. Repairs in areas of major corrosion and broken prestressed wires consisted of removing the earth cover, excavating a limited-length trench under a pipe unit, and completely removing the mortar coating and prestressing wire around the pipe for 360 deg. High-strength steel tendons were placed around the pipe and stressed to the initial prestressing force. Shotcrete was placed over the tendons and anchors, followed by backfilling. The two siphons were returned to service on Feb. 15, 1991. The repairs appear to be successful in restoring the concrete pipe to its initial design strength.
Click here to become an online Journal subscriber