In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Fiber-Reinforced Polymer Pipe Lining
Author(s): M. Ehsani and C. Pena
Publication: Concrete International
Appears on pages(s): 50-53
Keywords: cast-in-place, grinding, penstock, pressure test
Abstract:The low-pressure penstock at the El Encanto Hydroelectric Power Plant, located 75 miles (120 km) northwest of San José, Costa Rica was repaired using a fiber-reinforced polymer lining. The project required the installation of about 150,000 ft2 (14,000 m2) of FRP lining in a single phase. Prior to application of the fabric, an epoxy paste was applied to the top half of the penstock and a seal coat of epoxy resin was applied to the bottom half of the penstock. After they were saturated with resin, 50 in. (1270 mm) wide bands of fabric were rolled onto the prepared surface. The edges of the fabric bands were lapped in the circumferential and longitudinal directions to achieve full continuity of the FRP, and the edges of the laps were feathered with epoxy paste or resin.
The final step involved installation of an epoxy top coat as a cover for all the installed FRP. The project successfully passed a pressure test and was entered into service.
Click here to become an online Journal subscriber