In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Chat with Us Online Now
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Destruction of Concrete Water Tanks in a Severe Climate Due to Ice Lensing
Author(s): Christopher Rogers and Boguslaw Chojnacki
Publication: Special Publication
Appears on pages(s): 723-740
Keywords: absorption; air entrainment; climate; failure mechanisms; freeze-thaw durability; freezing; ice formation; low temperature; petrography; reinforced concrete; water tanks; General
Abstract:A concrete fish-breeding tank built near the north shore of Lake Superior failed during the first winter. The 250 mm thick concrete wall failed by cracking and delamination in the center of the concrete. The outside surfaces were generally unaffected. The concrete leaked water at such a rate that the tank became unusable. Spring-fed water inside the tank had been maintained at a constant temperature of 4.5 C. At this site, the mean daily temperature in December is -10 C; in January and February it is about -15 C. Minimum temperatures are commonly less than -30 C and may drop to -40 C. The concrete had been delivered by ready-mix trucks following a two-hour haul. Quality control on the site had been poor. The concrete in the failed areas was non-air-entrained and had a high water-cement ratio. Failure was attributed to formation of an ice lens within the permeable concrete.
Click here to become an online Journal subscriber