In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Chat with Us Online Now
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Vibration Isolated Foundations for Boiler Feedpumps
Author(s): Herbert A. Franklin
Publication: Special Publication
Appears on pages(s): 161-175
Keywords: concrete blocks; concrete construction; floors; foundations; machine bases; prestressed concrete; structural design; vibration isolators.
Abstract:This paper describes the design and construction of low-tuned, spring supported foundations for boiler feedpumps units installed in the Big Stone coal-fired power plant in South Dakota. Each system consists of a variable speed 9,500 HP (7084 Kw) steam turbine which drives a pair of feedpumps and is mounted on a prestressed concrete inertia block set on steel springs. This vibration isolation design required dynamic analysis of the inertia block systems since the variable speed pumps could present a range of forcing frequencies and hence a series of possible resonances. The concrete inertia blocks were prestressed in order to prevent cracking which could cause significant changes in the dynamic behavior. The concrete inertia blocks were fabricated and prestressed outside the turbine building. Each weighed about 96 tons (854 kN) and they were lifted into position on their steel springs on the operating floor level. The flexible isolation of the inertia blocks from the building floor facilitated the alignment of the machinery and the attachment of the piping. Vibration tests were conducted during plant start-up in order to anticipate potential problems and to verify dynamic characteristics. These units have now performed successfully for several years.
Click here to become an online Journal subscriber