In today’s market, it is imperative to be knowledgeable and have an edge over the competition. ACI members have it…they are engaged, informed, and stay up to date by taking advantage of benefits that ACI membership provides them.
Read more about membership
Become an ACI Member
Founded in 1904 and headquartered in Farmington Hills, Michigan, USA, the American Concrete Institute is a leading authority and resource worldwide for the development, dissemination, and adoption of its consensus-based standards, technical resources, educational programs, and proven expertise for individuals and organizations involved in concrete design, construction, and materials, who share a commitment to pursuing the best use of concrete.
American Concrete Institute
38800 Country Club Dr.
Farmington Hills, MI
Feedback via Email
Home > Publications > International Concrete Abstracts Portal
The International Concrete Abstracts Portal is an ACI led collaboration with leading technical organizations from within the international concrete industry and offers the most comprehensive collection of published concrete abstracts.
Title: Carbon FRP Strengthening of PCCP Aqueducts
Author(s): T. Alkhrdaji and J. Thomas
Publication: Special Publication
Appears on pages(s): 349-360
Keywords: carbon fibers; load testing; prestressed concrete cylindrical pipes (PCCP); upgrading; water main; waterstop
Abstract:To prevent future blowouts of sections of the 50-year-old pipe, the Providence Water Supply Board decided to evaluate the condition of a main water pipeline. Non-destructive testing (NDT) investigations revealed that certain sections of the pipe were potentially deficient due to corrosion and breakage of the prestressing system. Strengthening of deficient sections was necessary to maintain the pipeline operational. A carbon fiber in-situ lining appeared to be the fastest, least disruptive, and most cost-effective upgrade solution. The specialty concrete repair contractor conducted full-scale tests to validate optimum FRP repair and waterstop termination design. In these tests, after the carbon fiber liner was installed, the prestressing strands of the FRPstrengthened section were cut leaving the FRP to be the only reinforcement. The test pipe was progressively pressurized until failure occurred at approximately 2-1/2 times the pipe service and surge pressures. The full-scale test proved the integrity of the system beyond theoretical prediction and assured the owner that strength was added to the pipe sections. The lightweight, flexible carbon fiber material along with thorough planning helped overcome challenging working conditions and provided a fast and effective upgrade solution.
Click here to become an online Journal subscriber